“I have a Cabinet Cooler installed on my panel but it isn’t getting the temperature down cold enough. Can you quote me for a duplicate system to install on this panel?” This was a recent inquiry from a customer regarding an electrical enclosure that they had installed in their plant. The Cabinet Cooler was producing cold air, but not enough to keep the cabinet at their desired temperature. It would seem logical that they need additional capacity, right? While that could be the case, in this instance it most definitely was not.
When we get questions like this, we first want to take a closer look at the current installation. The cooling capacity for each system is published in our catalog. BUT, in order to rate a cooling capacity for any type of cooling system, some assumptions must be made. All Cabinet Coolers are specified with 70°F compressed air fed to the Cabinet Cooler at a pressure of 100 PSIG. In addition, each cooler has a specified volume of air that it must utilize in order to produce that rated cooling capacity. If any one of those parameters change, so does the overall cooling power.
In this particular case, the customer had installed a non-EXAIR pressure regulator just upstream of the cooler. Upon looking at the specifications for this regulator, it was found that the overall volume of air it can deliver was just 10% of the overall volume needed to produce the rated 1700 Btu/hr. They didn’t need another Cabinet Cooler System, they just needed to remove that restriction! Upon learning that it needed 100 PSIG, they removed the regulator and supplied full line pressure. No more heat alarms for that shift!
Rather than purchasing and installing an unnecessary system, they were able to get back up and running just by removing the problem upstream. At EXAIR, we want to make sure that you’re getting the most out of our products. Just because you call and inquire about a new purchase doesn’t necessarily mean that you need it. We’re here to help you determine if something is afoul with the current setup and make sure you have all of the knowledge necessary to rectify it.
We’re right in the middle of summer, and boy is it hot out there. If you have panels that are overheating and creating problems for you in your processes, give us a call. With Cabinet Cooler Systems ready to ship same day from stock (with properly sized regulators) you can have it fixed by tomorrow.