“I need one of your Cabinet Coolers for my control panel, the dimensions are 24″ H x 30″ W x 16″ D, what do you recommend?”. This is a very common inquiry we receive when discussing our Cabinet Cooler Systems for the first time with a potential customer. While it would be nice if it was a simple as using just the dimensions, there is more that goes in to making the proper selection.
Following explains how to go about calculating and choosing a Cabinet Cooler System. If, at any time, you prefer EXAIR to calculate and assist with your choice – contact our Application Engineering department and we will be happy to get you up and running.
Our Cabinet Coolers are sized by cooling capacity in Btu/hr., which range from our lowest of 275, up to our largest Dual System providing 5,600 Btu/hr. Now if you know the Watts loss , we can convert this over to Btu/hr. (Watts X 3.41 = Btu/hr.). If you are unsure, we need to determine the current heat load of the cabinet by using the dimensions, current temperatures (internal and external) and worst case external temperature and the desired temperature you are looking to maintain inside the enclosure. To simplify this process, we offer our Cabinet Cooler Sizing Guide.
The current internal and external temperature will determine one of your ΔT’s (temperature differential), which is used to determine a multiplier from the table below. We then take your maximum external temperature and your desired internal temperature to give us another ΔT and multiplier. Use the sq. ft. of the cabinet and multiplying it by the temperature conversion multipliers. Add these sums together to determine the total heat load in Btu/Hr. This value will help you to choose the proper Cabinet Cooler system to solve your heat problem.
Now that we have the heat load properly calculated, we need to know the NEMA class of the enclosure. We offer NEMA 12 for general use where there aren’t any corrosives or liquids present, NEMA 4 for wet or damp environments and NEMA 4X for wet, corrosive applications.
We offer Thermostatically Controlled Systems with available voltages of 120VAC, 240 VAC or 24VDC. This is the most efficient means of operation as the unit only operates when the internal desired temperature is exceeded. In addition, we also offer Continuous Operating Systems, providing constant cooling and positive pressure into the cabinet. Each system includes a filter separator for the supply line to keep water and dirt from entering the cabinet as well as duct tubing.
Of course, if you need any additional assistance, you can always contact one of our application engineers. If you can provide a little bit of information, we can do the calculating and get you on your way.