A critical component to optimal performance of any compressed air operated product is ensuring sufficient compressed air flow. Simply put, inadequate air flow won’t allow you to get the job done.
As compressed air moves through the distribution system, it encounters friction inside of the walls of the pipe, tube, hose, etc. The diameter of the pipe, length, number of direction changes, and finish surface of the inner wall all play a part in this. A drop in air pressure will occur as a result of this friction. In addition to pressure drops experienced due to the distribution system, they can also occur at the point of use.
When designing and maintaining your compressed air system, pressure measurements should be taken across varying points to identify (and fix) any issues before they create a greater problem down the road. According to the Compressed Air Challenge, these are the places you should take regular pressure measurements to determine your system operating pressure:
- Inlet to compressor (to monitor inlet air filter) vs. atmospheric pressure
- Differential across air/lubricant separator
- Interstage on multistage compressors
- At treatment equipment (dryers, filters, etc.)
- Various points across the distribution system
- Check pressure differentials against manufacturers’ specifications, if high pressure drops are noticed this indicates a need for service
*More recent compressors will measure pressure at the package discharge, which would include the separator and aftercooler.
Once you’ve taken these measurements, simply add the pressure drops measured and subtract that value from the operating range of your compressor. That figure is your true operating pressure at the point of use.
If your distribution system is properly sized and the pressure drops measured across your various equipment are within specifications, any pressure drop noticed at the point of use is indicative of an inadequate volume of air. This could be due to restrictive fittings, undersized air lines, hose, or tube, or an undersized air compressor. Check that the point of use product is properly plumbed to compressed air per the manufacturer’s specifications.
EXAIR Products are designed to minimize this pressure drop by restricting the flow of compressed air at the point of use. The more energy (pressure) that we’re able to bring to the point of use, the more efficient and effective that energy will be. The photo below shows two common examples of inefficient compressed air usage. With an open-ended blow off, a pressure drop occurs upstream inside of the supply line. If you were to measure the pressure directly at the point of use, while in operation, you’d find that the pressure is significantly lower than it is at the compressor or further up the line. In the other photo with modular style hose, some pressure is able to be built up but if it gets too high the hose will blow apart. These types of modular style hose are not designed to be used with compressed gases.
EXAIR’s Super Air Nozzles, on the other hand, keep the compressed air pressure right up to the point of discharge and minimize the pressure drop. This, in addition to the air entrained, allows for a high force while maximizing efficiency. If you’d like to talk about how an EXAIR Intelligent Compressed Air Product could help to minimize pressure drop in your processes give us a call.