## Consider these Variables When Choosing Compressed Air Pipe Size

Here on the EXAIR blog we discuss pressure drops, correct plumbing, pipe sizing, and friction losses within your piping system from time to time.   We will generally even give recommendations on what size piping to use.  These are the variables that you will want to consider when selecting a piping size that will suit your need and give the ability to expand if needed.

The variables to know for a new piping run are as follows.

• Flow Rate (SCFM) of demand side (products needing the supplied compressed air)
• System Pressure (psig) – Safe operating pressure that will account for pressure drops.
• Minimum Operating Pressure Allowed (psig) – Lowest pressure permitted by any demand side point of use product.
• Total Length of Piping System (feet)
• Piping Cost (\$)
• Installation Cost (\$)
• Operational Hours ( hr.)
• Electical Costs (\$/kwh)
• Project Life (years) – Is there a planned expansion?

An equation can be used to calculate the diameter of pipe required for a known flow rate and allowable pressure drop.   The equation is shown below.

A = (144 x Q x Pa) / (V x 60 x (Pd + Pa)
Where:
A = Cross-Sectional are of the pipe bore. (sq. in.).
Q = Flow rate (cubic ft. / min of free air)
Pa = Prevailing atmospheric absolute pressure (psia)
Pd  = Compressor discharge gauge pressure (psig)
V = Design pipe velocity ( ft/sec)

If all of these variables are not known, there are also reference charts which will eliminate the variables needed to total flow rate required for the system, as well as the total length of the piping. The chart shown below was taken from EXAIR’s Knowledge Base.