If you watched the Webinar we hosted recently (if not, Watch It here) then you know that the EXAIR Cabinet Cooler System is an intelligent solution for electrical enclosure cooling. The use of a Thermostat Control system is a key component to a system that provides the needed cooling while keeping compressed air usage to a minimum. There are several choices available, and I will cover those for you today.
The thermostat control systems are the most effective way to operate a Cabinet Cooler. They work by activating the the cooler only when the internal temperature of the enclosure reaches a preset, critical level. Thermostat controlled cooler systems are the best option when a cabinet will experience fluctuating heat loads, caused by operational, environmental, and seasonal changes.
Cabinet Cooler Systems that are ordered from the factory with thermostat control include a solenoid valve and thermostat. The solenoid valve is available in 110-120VAC, 50/60 Hz, 240VAC, 50/60 Hz, and 24VDC and is UL Listed and CE and RoHS compliant. The thermostat is rated for 24V-240V AC or DC, 50/60 Hz and is UL Recognized and CSA Certified.
The thermostat is factory set at 95°F (35°C). It will typically hold an internal cabinet temperature to +/- 2°F (1°C). The thermostat can be adjusted up or down if a different internal temperature is desired by turning the slotted temperature adjusting sleeve, with a 1/16 turn being approximately a 5°F change.
The solenoid and thermostat components are rated to match and maintain the Cabinet Cooler System and cabinet NEMA rating, and can be NEMA 12, NEMA 4 or NEMA 4X. A Thermostat Control can be added to an existing Continuous Operation Cabinet Cooler System, please consult the factory for help in selecting the right kit.
If you have any questions about the Cabinet Coolers and Thermostat Options or any of the EXAIR Intelligent Compressed Air® Products, feel free to contact EXAIR and myself or one of our Application Engineers can help you determine the best solution.