An EXAIR Cabinet Cooler® System with either the Thermostat Control or the Electronic Temperature Control (ETC) option includes a temperature measuring device that is used to control the operation of the Cabinet Cooler System to maintain the set-point temperature.
For most industrial enclosure cooling applications, a temperature of 95°F (35°C) is sufficient to be below the rated maximum operating temperature of the electrical components inside the cabinet. EXAIR Thermostats are preset to 95°F (35°C) and are adjustable. Maintaining the cabinet at 95°F (35°C) will keep the electronics cool and provide long life and reduced failures due to excessive heat. But if 95°F (35°C) is good, why not cool the cabinet to 70°F (21.1°C)?
When cooling an enclosure to a lower temperature, two things come into play that need to be considered. First, the amount of external heat load (the heat load caused by the environment) is increased. Using the table below, we can see the effect of cooling a cabinet to the lower temperature. For a 48″ x 36″ x 18″ cabinet, the surface area is 45 ft² (4.18 m²). If the ambient temperature is 105°F (40.55°C), we can find from the table the factors of 3.3 BTU/hr/ft² and 13.8 BTU/hr/ft² for the Temperature Differentials of 10°F (5.55°C) and 35°F (19.45°C). The factor is multiplied by the cabinet surface area to get the external heat load. The heat load values calculate to be 148.5 BTU/hr and 621 BTU/hr, a difference of 472.5 BTU/hr (119.1 kcal/hr)
The extra external heat load of 472.5 BTU/hr (119.1 kcal/hr) will require the Cabinet Cooler System to run more often and for a longer duration to effectively remove the additional heat. This will increase, unnecessarily, the operating costs of the cooling operation.
The other factor that must be considered when cooling an enclosure to a lower temperature is that the Cabinet Cooler cooling capacity rating is effected. I won’t go into the detail in this blog, but note that a 1,000 BTU/hr Cabinet Cooler (rated for 95°F (35°C cooling) working to cool a cabinet down to 70°F (21.1°C) instead of 95°, has a reduced cooling capacity of 695 BTU/hr (174 kcal/hr). The reduction is due to the cold air being able to absorb less heat as the air rises in temperature to 70°F instead of 95°F.
In summary – operating a Cabinet Cooler System at 95°F (35°C) provides a level cooling that will keep sensitive electronics cool and trouble-free, while using the least amount of compressed air possible. Cooling to below this level will result in higher operation costs.
If you have questions about Cabinet Cooler Systems or any of the 15 different EXAIR Intelligent Compressed Air® Product lines, feel free to contact EXAIR and myself or any of our Application Engineers can help you determine the best solution.
Send me an email
Find us on the Web
Like us on Facebook