It’s easy to know that EXAIR’s vortex tubes can be used to cool down parts and other items, but did you know that our air knifes can be used to cool down these same things? It’s the same process that we do every day to cool down hot food by blowing on it. Every molecule and atom can carry a set amount of energy which is denoted by physical property called Specific Heat (Cp); this value is the ration of energy usually in Joules divided by the mass multiplied by the temperature (J/g°C). Knowing this value for one can calculate the amount of air required to cool down the object.
Starting out you should note a few standard values for this rough calculation; these values are the specific heat of Air and the specific heat of the material. Using these values and the basic heat equation we can figure out what the amount of energy is required to cool. The specific heat for dry air at sea level is going to be 1.05 J/g*C which is a good starting point for a rough calculation; as for the specific heat of the material will vary depending on the material used and the composition of the material.
If you have any questions about compressed air systems or want more information on any EXAIR’s of our products, give us a call, we have a team of Application Engineers ready to answer your questions and recommend a solution for your applications.
Cody Biehle Application Engineer EXAIR Corporation Visit us on the Web Follow me on Twitter Like us on Facebook
Cabinet Cooler systems eliminate heat related problems by providing a temperature controlled environment inside of electrical enclosures. Typically set to maintain 95F (but also adjustable) a Cabinet Cooler system can withstand harsh, remote environments with little maintenance. They cool heat loads up to 5600 Btu/Hr and are UL listed to maintain your cabinet’s NEMA integrity.
Compressed air enters the vortex tube powered Cabinet Cooler and is converted into two streams, one hot and one cold. Hot air from the vortex tube is muffled and exhausted through the vortex tube exhaust. The cold air is discharged into the cabinet through the included cold air distribution kit. The displaced hot air in the cabinet rises and exhausts to atmosphere through the cabinet cooler body. The control cabinet is both cooled and purged with cool, clean air. Outside air is never able to enter the control panel.
EXAIR’s compressed air operated, Cabinet Cooler Systems are a low cost, reliable way to cool and purge electronic control panels. There are no moving parts to wear out and no filters to replace, eliminating the need for constant monitoring.
NEMA Type 12 (IP54) and NEMA 4 and 4X (IP66) models are available that are very compact and mount in just minutes through an ordinary electrical knockout.
Available in a wide range of cooling capacities, ranging from 275 Btu/hr. for our smallest system, up to 5,600 Btu/hr. for our largest Dual System.
Thermostat control systems are the most efficient way to operate a Cabinet Cooler as they limit compressed air use by operating only when the temperature inside the enclosure approaches critical levels. Continuous Operating Systems are recommend when constant cooling and constant positive pressure inside the panel is required.
Thermostat controlled Cabinet Cooler Systems are the best option when experiencing fluctuating heat loads caused by environment or seasonal changes. Thermostatically Controlled Systems include a Cabinet Cooler, adjustable thermostat, solenoid valve, cold air distribution kit consisting of tubing and self adhesive clips to duct the cold air inside the panel and a filter separator to remove any water or contaminants from the supply.
If you would like to discuss our cabinet cooler systems or any of EXAIR’s engineered solutions, I would enjoy hearing from you…give me a call.
By using only a source of compressed air, theCold Gun and High Power Cold Gun produces a stream of clean, cold air 50°F (28°C) below your compressed air supply temperature. The Cold Gun is very quiet at only 70 dBA and has no moving parts to wear out. Just supply it with clean compressed air and it’s maintenance free.
How does it work, and what are the benefits?
The Cold Gun uses compressed air to produce a stream of clean, cold air at 50°F (28°C) below supply air temperature. Generally this will be 20°F-30°F outlet temperature.
They use Vortex Tubetechnology…no moving parts to wear out.
Instant cold air flow with no moving parts!
Cold flow and temperature are preset to optimize cooling capability, and are non-adjustable to prevent freeze-up during use.
Eliminates the expense of both the purchase & disposal of cutting fluids when replacing expensive mist systems.
Removes the potential for health problems associated with breathing mist & vapors, and the safety issue of slipping on a wet floor.
Cold Gun Aircoolant System selection is easy & straightforward…we offer a standard, and a High Powerversion to meet your specific needs.
We also offer Single & Dual Point Hose Kits, to further meet the needs of your application.
One of the best applications I have seen with our cold gun came from a customer in Peru. They are a gold mining operation and they were having trouble with the liquid they were using to cool a saw. Read all about it here!
If you have an application that you believe would be better served by the use of an EXAIR Cold Gun, give us a call.
For most industrial enclosure cooling applications, a temperature of 95°F (35°C) is sufficient to be below the rated maximum operating temperature of the electrical components inside the cabinet. EXAIR Thermostats are preset to 95°F (35°C) and are adjustable. Maintaining the cabinet at 95°F (35°C) will keep the electronics cool and provide long life and reduced failures due to excessive heat. But if 95°F (35°C) is good, why not cool the cabinet to 70°F (21.1°C)?
When cooling an enclosure to a lower temperature, two things come into play that need to be considered. First, the amount of external heat load (the heat load caused by the environment) is increased. Using the table below, we can see the effect of cooling a cabinet to the lower temperature. For a 48″ x 36″ x 18″ cabinet, the surface area is 45 ft² (4.18 m²). If the ambient temperature is 105°F (40.55°C), we can find from the table the factors of 3.3 BTU/hr/ft² and 13.8 BTU/hr/ft² for the Temperature Differentials of 10°F (5.55°C) and 35°F (19.45°C). The factor is multiplied by the cabinet surface area to get the external heat load. The heat load values calculate to be 148.5 BTU/hr and 621 BTU/hr, a difference of 472.5 BTU/hr (119.1 kcal/hr)
The extra external heat load of 472.5 BTU/hr (119.1 kcal/hr) will require the Cabinet Cooler System to run more often and for a longer duration to effectively remove the additional heat. This will increase, unnecessarily, the operating costs of the cooling operation.
The other factor that must be considered when cooling an enclosure to a lower temperature is that the Cabinet Cooler cooling capacity rating is effected. I won’t go into the detail in this blog, but note that a 1,000 BTU/hr Cabinet Cooler (rated for 95°F (35°C cooling) working to cool a cabinet down to 70°F (21.1°C) instead of 95°, has a reduced cooling capacity of 695 BTU/hr (174 kcal/hr). The reduction is due to the cold air being able to absorb less heat as the air rises in temperature to 70°F instead of 95°F.
In summary – operating a Cabinet Cooler System at 95°F (35°C) provides a level cooling that will keep sensitive electronics cool and trouble-free, while using the least amount of compressed air possible. Cooling to below this level will result in higher operation costs.
If you have questions about Cabinet Cooler Systems or any of the 15 different EXAIR Intelligent Compressed Air® Product lines, feel free to contact EXAIR and myself or any of our Application Engineers can help you determine the best solution.