## Intermediate Storage Tanks & How To Size Them

When evaluating processes that utilize compressed air and adhering to the Six Steps to Compressed Air Optimization, intermediate storage proves to be a critical role coming in at step number five. Intermediate storage tanks may already be in place within your facility and often times can be implemented as modifications to aid existing lines that are struggling to maintain proper availability of compressed air to keep the line at peak performance.

When determining whether or not a production line or point of use compressed air operation would benefit from a receiver tank/intermediate storage we would want to evaluate whether the demand for compressed air is intermittent.  Think of a receiver tank as a capacitor in an electrical circuit or a surge tank in a water piping system.  These both store up energy or water respectively to deliver to during a short high demand period then slowly charge back up from the main system and prepare for the next high demand.   If you look from the supply point it will see a very flattened demand curve, if you look from the application side it still shows a wave of peak use to no use.

One of the key factors in intermediate storage of compressed air is to appropriately size the tank for the supply side of the system as well as the demand of the application.  The good news is there are equations for this.  To determine the capacity, use the equation shown below which is slightly different from sizing your main compressed air storage tank.  The formulate shown below is an example.

Where:

V – Volume of receiver tank (ft3 / cubic feet)

T – Time interval (minutes)

C – Air demand for system (cubic feet per minute)

Cap – Supply value of inlet pipe (cubic feet per minute)

Pa – Absolute atmospheric pressure (PSIA)

P2 – Regulated Pressure (PSIG)

One of the main factors when sizing point of use intermediate storage is, they are being supplied air by smaller branch lines which cannot carry large capacities of air.  That limits your Cap value. The only way to decrease the V solution is to increase your Cap. The other key point is to ensure that all restrictions feeding into the tank and from the tank to your point of use are minimized in order to maintain peak performance.

If there are intermittent applications that are struggling to keep up with the production demands within your system, please reach out and speak with an Application Engineer.  We are always here to help and we may even be able to help you lower the demand needed by utilizing an engineered point of use compressed air solution.

Brian Farno
Application Engineer
BrianFarno@EXAIR.com
@EXAIR_BF

## Why Start a Leak Prevention Program?

All compressed air systems will have some amount of leakage. It is a good idea to set up a Leak Prevention Program.  Keeping the leakage losses to a minimum will save on compressed air generation costs, and reduce compressor operation time which can extend its life and lower maintenance costs.

The Compressed Air Challenge estimates an individual compressed air leak can cost thousands of dollars per year when using \$0.07/kWh.

• 1/16″ diameter hole in excess of \$700/year
• 1/8″ hole in excess of \$2900/year
• 1/4″ hole in excess of \$11,735 per year

There are generally two types of leak prevention programs:

• Leak Tag type programs
• Seek-and-Repair type programs

Of the two types, the easiest would be the Seek-and-Repair method.  It involves finding leaks and then repairing them immediately. For the Leak Tag method, a leak is identified, tagged, and then logged for repair at the next opportune time.

A successful Leak Prevention Program consists of several important components:

• Document your Starting Compressed Air Use – knowing the initial compressed air usage will allow for comparison after the program has been followed for measured improvement.
• Establishment of initial leak loss – See this blog for more details.
• Determine the cost of air leaks – One of the most important components of the program. The cost of leaks can be used to track the savings as well as promote the importance of the program. Also a tool to obtain the needed resources to perform the program.
• Find the leaks – Leaks can be found using many methods.  Most common is the use of an Ultrasonic Leak Detector, like the EXAIR Model 9061.  See this blog for more details. An inexpensive handheld meter will locate a leak and indicate the size of the leak.

• Record the leaks – Note the location and type, its size, and estimated cost. Leak tags can be used, but a master leak list is best.  Under Seek-and-Repair type, leaks should still be noted in order to track the number and effectiveness of the program.
• Plan to repairs leaks – Make this a priority and prioritize the leaks. Typically fix the biggest leaks first, unless operations prevent access to these leaks until a suitable time.
• Record the repairs – By putting a cost with each leak and keeping track of the total savings, it is possible to provide proof of the program effectiveness and garner additional support for keeping the program going. Also, it is possible to find trends and recurring problems that will need a more permanent solution.
• Compare and publish results – Comparing the original baseline to the current system results will provide a measure of the effectiveness of the program and the calculate a cost savings. The results are to be shared with management to validate the program and ensure the program will continue.
• Repeat As Needed – If the results are not satisfactory, perform the process again. Also, new leaks can develop, so a periodic review should be performed to achieve and maintain maximum system efficiency.

An effective compressed air system leak prevention and repair program is critical in sustaining the efficiency, reliability, and cost effectiveness of an compressed air system.

If you have questions about a Leak Prevention Program or any of the 16 different EXAIR Intelligent Compressed Air® Product lines, feel free to contact EXAIR and myself or any of our Application Engineers can help you determine the best solution.

Jordan Shouse
Application Engineer
Send me an email
Find us on the Web

## Basics of the Compressor Room

EXAIR Corporation has staked our reputation on a keen ability to help you get the most out of your compressed air system since 1983.  Now, the bulk of our expertise lies in the implementation and proper use of engineered products on the demand side, but we fully recognize that there are critical elements for optimization on the supply side too.  And that, quite literally, starts in the compressor room.  This is not an exhaustive, specifically detailed list, but here are some you might consider to get the most from the (again, quite literally) beginning:

• Location.  If you’re building a new facility, or doing a major rehab of your existing one, having the compressor room as close as practical to the point(s) of use is best, IF all other things are equal.  You’ll use less pipe if you don’t have to run it so far.  You’ll also be able to use smaller diameter lines because you won’t have to worry about line loss (pressure drop due to friction as the air flows through the total length) as much.
• Location part 2.  If all other things are NOT equal, having the compressor room close to the point of use may not be best for you.
• Your air compressor pulls in air from the immediate environment.  It’s better to go with longer and bigger pipe in your distribution system than it is to put your compressor in a location where it’ll pull in dust & particulate from grinding operations, humidity from a boiler plant, fumes from chemical production, etc.
• There are some pretty darn quiet air compressors out there, but there are some pretty loud ones too.  Especially in small to mid size facilities, putting the compressor in an area that upsizes the required piping is still likely a better idea, due to the downsizing of the noise levels that personnel will be exposed to.
• Environment.  No matter where your compressor is located, the machine itself should be protected from heat and other harsh environmental elements.  That means if it’s inside the plant, the compressor room should be adequately ventilated.  In some situations, the compressor may be best installed outside the plant, in its own building or protective structure.  This should be designed to protect against solar load…in addition to the high temperature associated with a hot summer day, the sun’s rays beating down on your air compressor will radiate a tremendous amount of heat into it.
• Filtration.  Whatever is in the air in your compressor room is going to get into your compressed air.  This is doubly problematic: particulate debris can damage the air compressor’s moving parts, and it can likewise damage your pneumatic cylinders, actuators, tools, motors, etc. as well.  Make sure the intake of your compressor is adequately filtered.
• Maintenance.  Air compressors, like any machinery with moving parts, require periodic preventive maintenance, and corrective maintenance when something inevitably breaks down.  There should be adequate space factored in to your compressor room’s layout for this.  The only thing worse than having to fix something is not having the room to fix it without taking other stuff apart.

These are a few things to consider on the supply end.  If you’d like to talk about how to get the most out of your compressed air system, EXAIR is keen on that.  Give us a call.

Russ Bowman
Application Engineer
EXAIR Corporation
Visit us on the Web

## How to Calculate the Cost of Leaks

Leaks are a hidden nuisance in a compressed air system that can cause thousands of dollars in electricity per year. These leaks on average can account for up to 30% of the operation cost of a compressed air system. A leak will usually occur at connection joints, unions, valves, and fittings. This not only is a huge waste of energy but it can also cause a system to lose pressure along with lowering the life span of the compressor since it will have to run more often to make up for the loss of air from the leak.

There are two common ways to calculate how much compressed air a system is losing due to leaks. The first way is to turn off all of the point of use compressed air devices; once this has been complete turn on the air compressor and record the average time that it takes the compressor to cycle on and off. With the average cycle time you can calculate out the total percentage of leakage using the following formula.

The second method is to calculate out the percentage lost using a pressure gauge downstream from a receiver tank. This method requires one to know the total volume in the system to accurately estimate the leakage from the system. Once the compressor turns on wait until the system reaches the normal operating pressure for the process and record how long it takes to drop to a lower operating pressure of your choosing. Once this has been completed you can use the following formula to calculate out the total percentage of leakage.

The total percentage of the compressor that is lost should be under 10% if the system is properly maintained.

Once the total percentage of leakage has been calculated you can start to look at the cost of a single leak assuming that the leak is equivalent to a 1/16” diameter hole. This means that at 80 psig the leak is going to expel 3.8 SCFM. The average industrial air compressor can produce 4 SCFM using 1 horsepower of energy. Adding in the average energy cost of \$0.25 per 1000 SCF generated one can calculate out the price per hour the leak is costing using the following calculation.

If you base the cost per year for a typical 8000 hr. of operating time per year you are looking at \$480 per year for one 1/16” hole leak. As you can see the more leaks in the system the more costly it gets. If you know how much SCFM your system is consuming in leaks then that value can be plugged into the equitation instead of the assumed 3.8 SCFM.

If you’d like to discuss how EXAIR products can help identify and locate costly leaks in your compressed air system, please contact one of our application engineers at 800-903-9247.

Cody Biehle
Application Engineer
EXAIR Corporation
Visit us on the Web

## Compressed Air Efficiency – How It Benefits Business

It is estimated that typically plants can waste up to 30 percent of their generated compressed air and that cost is substantial.  Considering the average cost to generate compressed air here in the Midwest is .25 cents per 1,000 Standard Cubic Feet, that translates into .075 cents for every .25 cents spent!  Compounded with the fact that energy costs have doubled in the last five years, it couldn’t be a better time to make your air compressor system more efficient.

The following steps will help you save air and in turn save money.

1. Measure the air consumption to find sources that use a lot of compressed air.

Knowing where you stand with your compressed air demand is important to be able to quantify the savings once you begin to implement a compressed air optimization program. Placing a value upon your compressed air consumption will also allow you to place a value on its costs and the savings you will reap once you start to reduce your consumption. (EXAIR’s Digital Flow Meter)

1. Find and fix the leaks in your compressed air system.

Not fixing your compressed air system leaks can cause your system pressure to fluctuate and affect your equipment negatively. It may cause you to run a larger compressor than necessary for your compressed air needs and raise your total costs. Or it could cause your cycle and run times to increase which leads to increased maintenance to the entire system. (EXAIR’s Ultrasonic Leak Detector)

1. Upgrade your blow off, cooling and drying operations using engineered compressed air products.

Your ordinary nozzle with a through hole and a cross drilled hole can be an easy choice based upon price, but if you do not consider the operating cost you do not really know how much it is costing you. An Engineered Air Nozzle will pay for itself and lower operating costs quickly. Engineered Air Nozzles are the future of compressed air efficiency and are made to replace ordinary nozzles, homemade nozzles and open line blow offs. Engineered Nozzles reduce air consumption and noise levels; ordinary nozzles cannot compete. Engineered Nozzles maintain safety features and can qualify for an energy savings rebate from a local utility; ordinary nozzles fall short. Open blow off or homemade blow off applications typically violate OSHA safety standards; Engineered Nozzles do not.  (EXAIR’s Air Nozzles)

1. Turn off the compressed air when it is not in use.

Automated solutions add solenoid valves and run them from your machine controls. If the machine is off, or the conveyor has stopped – close the solenoid valve and save the air.  And blow off applications can benefit from any space in between parts by turning the air off during the gaps with the aid of a sensor and solenoid. (EXAIR’s automated  Electronic Flow Control)

1. Use intermediate storage of compressed air near the point of use.

Also known as secondary receivers, intermediate air storage is especially effective when a system has shifting demands or large volume use in a specific area. Intermediate storage is the buffer between a large demand event and the output of your compressor. The buffer created by intermediate storage (secondary receiver) prevents pressure fluctuations which may impact other end use operations and affect your end product quality. (EXAIR’s Receiver Tanks)

1. Control the air pressure at the point of use to minimize air consumption.

This is a very simple and easy process, all it requires is a pressure regulator. Installing a pressure regulator at all of your point of use applications will allow you to lower the pressure of these applications to the lowest pressure possible for success. Lowering the pressure of the application also lowers the air consumption. And it naturally follows that lower air consumption equals energy savings. (EXAIR’s Pressure Regulators)

By increasing your awareness of the health of your air compressor system and implementing a PM program you can significantly reduce your costs from wasted energy and avoid costly down time from an out of service air compressor.

If you would like to discuss improving your compressed air efficiency or any of EXAIR’s engineered solutions, I would enjoy hearing from you…give me a call.

Jordan Shouse
Application Engineer
Send me an email
Find us on the Web

## The Case For Desiccant Compressed Air Dryers

Most people are familiar with desiccant from the small packets we find enclosed with a new pair of shoes, in a bag of beef jerky, or in some medication bottles.  These packets almost always say “Do Not Eat,” and I get that for the ones in the beef jerky or the pill bottles, but I just don’t understand why they put it on the desiccant packets bound for a shoe box…

Anyway, desiccant (in MUCH larger volumes than the household examples above) are also used to get water vapor out of compressed air.  Desiccant dryers are popular because they’re effective and reliable.  The most common design consists of two vertical tanks, or towers, filled with desiccant media – usually activated alumina or silica gel.

These materials are prone to adsorption (similar to absorption, only it’s a physical process instead of a chemical one) which means they’re good at trapping, and holding, water.  In operation, one of these towers has air coming in it straight from the compressor (after it’s become pressurized, remember, it still has just as much water vapor in it as it did when it was drawn in…up to 5% of the total gas volume.)

When that tower’s desiccant has adsorbed water vapor for long enough (it’s usually controlled by a timer,) the dryer controls will port the air through the other tower, and commence a restoration cycle on the first tower.  So, one is always working, and the other is always getting ready for work.

There are three methods by which the desiccant media can be restored:

• Regenerative Desiccant Dryers send a purge flow of dry air (fresh from the operating tower’s discharge) through the off-line tower’s desiccant bed.  This dry air flow reverses the adsorption process, and carries the water away as it’s exhausted from the dryer.  This is simple and effective, but it DOES use a certain amount of your compressed air.
• Heat Of Compression Desiccant Dryers use the heat from pressurized air straight from the compressor(s).  This hot air is directed through one tower, where it removes moisture from the desiccant.  It then flows through a heat exchanger where it’s cooled, condensing the moisture, before it flows through the other tower to remove any remaining moisture.  This method doesn’t add to your compressed air usage, but it only works with oil-free compressors.
• The third method uses a hot air blower to flow heated air through the off-line desiccant bed.  It’s similar to the Regenerative type, but it doesn’t use compressed air.  However, they DO require a certain amount of wattage for the heater…remember, electricity isn’t cheap either.

As an EXAIR Application Engineer, it’s my job to help you get the most out of our products, and your compressed air system.  If you have questions about compressed air, call me.

Russ Bowman
Application Engineer
EXAIR Corporation
Visit us on the Web

## About Compressed Air Dryers – What Are They and Why Use Them

All atmospheric air contains some amount of water vapor.  When air is then cooled to saturation point, the vapor will begin to condense into liquid water. The saturation point is the condition where the the air can hold no more water vapor. The temperature at which this occurs is knows as the dew point.

When ambient air is compressed, heat is generated and the air becomes warmer. In industrial compressed air systems, the air is then routed to an aftercooler, and condensation  begins to take place. To remove the condensation, the air then goes into separator which traps the liquid water. The air leaving the aftercooler is typically saturated at the temperature of the discharge, and any additional cooling that occurs as the air is piped further downstream will cause more liquid to condense out of the air. To address this condensation, compressed air dryers are used.

It is important to dry the air and prevent condensation in the air. Many usages of the compressed air are impacted by liquid water being present. Rust and corrosion can occur in the compressed air piping, leading to scale and contamination at point -of -use processes. Processes such as drying operations and painting would see lower quality if water was deposited onto the parts.

There are many types of dryers – (see recent blogs for more information)

• Refrigerant Dryer – most commonly used type, air is cooled in an air-to-refrigerant heat exchanger.
• Regenerative-Desiccant Type – use a porous desiccant that adsorbs (adsorb means the moisture adheres to the desiccant, the desiccant does not change, and the moisture can then be driven off during a regeneration process).
• Deliquescent Type – use a hygroscopic desiccant medium that absorbs (as opposed to adsorbs) moisture. The desiccant is dissolved into the liquid that is drawn out. Desiccant is used up, and needs to be replaced periodically.
• Heat of Compression Type – are regenerative desiccant dryers that use the heat generated during compression to accomplish the desiccant regeneration.
• Membrane Type– use special membranes that allow the water vapor to pass through faster than the dry air, reducing the amount water vapor in air stream.

The air should not be dried any more than is needed for the most stringent application, to reduce the costs associated with the drying process. A pressure dew point of 35°F to 38°F (1.7°C to 3.3°C) often is adequate for many industrial applications.  Lower dew points result in higher operating costs.

If you have questions about compressed air systems and dryers or any of the 15 different EXAIR Intelligent Compressed Air® Product lines, feel free to contact EXAIR and myself or any of our Application Engineers can help you determine the best solution.

Brian Bergmann
Application Engineer
Send me an email
Find us on the Web