All atmospheric air contains some amount of water vapor. When air is then cooled to saturation point, the vapor will begin to condense into liquid water. The saturation point is the condition where the the air can hold no more water vapor. The temperature at which this occurs is knows as the dew point.
When ambient air is compressed, heat is generated and the air becomes warmer. In industrial compressed air systems, the air is then routed to an aftercooler, and condensation begins to take place. To remove the condensation, the air then goes into separator which traps the liquid water. The air leaving the aftercooler is typically saturated at the temperature of the discharge, and any additional cooling that occurs as the air is piped further downstream will cause more liquid to condense out of the air. To address this condensation, compressed air dryers are used.
It is important to dry the air and prevent condensation in the air. Many usages of the compressed air are impacted by liquid water being present. Rust and corrosion can occur in the compressed air piping, leading to scale and contamination at point -of -use processes. Processes such as drying operations and painting would see lower quality if water was deposited onto the parts.
There are many types of dryers – (see recent blogs for more information)
- Refrigerant Dryer – most commonly used type, air is cooled in an air-to-refrigerant heat exchanger.
- Regenerative-Desiccant Type – use a porous desiccant that adsorbs (adsorb means the moisture adheres to the desiccant, the desiccant does not change, and the moisture can then be driven off during a regeneration process).
- Deliquescent Type – use a hygroscopic desiccant medium that absorbs (as opposed to adsorbs) moisture. The desiccant is dissolved into the liquid that is drawn out. Desiccant is used up, and needs to be replaced periodically.
- Heat of Compression Type – are regenerative desiccant dryers that use the heat generated during compression to accomplish the desiccant regeneration.
- Membrane Type– use special membranes that allow the water vapor to pass through faster than the dry air, reducing the amount water vapor in air stream.
The air should not be dried any more than is needed for the most stringent application, to reduce the costs associated with the drying process. A pressure dew point of 35°F to 38°F (1.7°C to 3.3°C) often is adequate for many industrial applications. Lower dew points result in higher operating costs.
If you have questions about compressed air systems and dryers or any of the 15 different EXAIR Intelligent Compressed Air® Product lines, feel free to contact EXAIR and myself or any of our Application Engineers can help you determine the best solution.