Here at EXAIR, our vortex tubes are offered in two separate series. The reason for this is to optimize the performance of the cold air temperature drop when operating with opposite ends of the cold fraction chart. The maximum refrigeration vortex tubes, 32xx series, perform optimally when they are set to a greater than 50% cold fraction. The maximum cold temp vortex tubes, 34xx series, perform optimally when they are set to a less than or equal to 50% cold fraction. The cold fraction is discussed more in-depth within this link from Russ Bowman, Vortex Tube Cold Fractions Explained. This blog is going to explain a little further why one series of vortex tubes would be chosen for an application over another.
Maximum refrigeration (32xx) vortex tubes are the most commonly discussed of the two types when discussing the optimal selection of the vortex tube for an application. The 32xx series vortex tubes achieve a maximum refrigeration output when operated at 100 psig inlet pressure with around 80% cold fraction. This would give a temperature drop from incoming compressed air temperature of 54°F (30°C). The volumetric flow rate of cold air will be 80% of the input flow which means only 20% is being exhausted as warm exhaust air. By keeping the flow rate higher the air is able to cool a higher heat load and is the reason the vortex tube is given a BTU/hr cooling capacity.
Maximum cold temperature (34xx) tubes are less common as their applications are a little more niche and require a very pinpoint application. Rather than changing the temperature inside of a cooling tunnel or cooling an ultrasonic welding horn, the max cold temp vortex tube is going to have a minimum cold flow rate, less than 50% of input volumetric flow. This minimal flow will be at temperature drops up to 129°F (71.1°C) from the incoming compressed air temperature. This air is very cold and at a low flow. A 20% cold fraction exhausts 80% of the input volume as hot air. This type of volume would be ideal for sensor cooling, pinpoint cooling of a slow-moving operation, or thermal testing of small parts.
In the end, EXAIR vortex tubes perform their task of providing cold or hot air without using any refrigerants or moving parts. To learn more about how they work, check out this blog from Russ Bowman. If you want to see how to change the cold fraction, check out the video below. If you would like to discuss anything compressed air related, contact an application engineer, we are always here to help.