Leaks, and not the kind you see on a cooking show, are never good. Before you comment, yes I know the vegetable is spelled leek, that’s just the strength of my dad jokes. The point of this post is actually discussing leaks, mainly of the compressed air variety. All leaks cost. I recently found a leak within my home which was accounting for around a 20% increase in my water bill. Sad to say that it took a few months to locate, and solve the issue. Over the years, I’ve seen many facilities deal with common leak problems like being unable to leave their compressed air pipes energized over night because the parasitic draw will drain the entire system. That’s a problem!
If the leaks are present when nothing is being utilized, then that means parasitic draw is happening on the system. This is when energy that is being converted into compressed air isn’t used but instead, leaking out to atmospheric conditions. These parasitic draws are not always easy to locate, so over the years I’ve had to help a few customers address this problem. One in particular stands out, so I am going to share how we honed in on the leak and ultimately gave them days without a shutdown.
The conversation all started with a customer asking about how our Digital Flowmeters work, and if they could be used to determine which production line is using the most air, and more importantly why their production line shuts down for low air pressure. After I explained how we would select their infeed pipe size as well as size a meter that would fit each machine infeed, we got to talking about the shut down sequence.
The approach they took to solving the issue was to first capture the flowrate of the entire system and then to evaluate the flowrates of each segment of their plant. From there, we would install flowmeters on the higher usage sectors, and drill down to each machine for the finite analysis. They could then go through all the other production lines and generate a full facility consumption profile. To start, they found one packaging line that was using a considerably higher volume of air throughout their first shift than any other line and than any other shift.
Once they started breaking down the high demand production line they found one leg of the production line which had a spike in usage at the same time every day. The trick was they couldn’t find a machine with high usage, that is until they traced all of the piping and found a filter bag house on the roof that had been added to the line at some point. This wasn’t documented and had a piece of pipe that had failed causing an open dump during the cleaning cycle every day at 2:30 in the afternoon.
This was all made possible by setting up multiple flowmeters with wireless capabilities so they could document and compare the usages between machines and production lines ultimately giving them a considerable amount of production time back into the day by fixing a broken pipe that caused daily shutdowns.
If you would like to discuss how to layout a compressed air monitoring system in your facility or the best way to track down the cause of some leaks and high compressed air demand, contact an Application Engineer.
1 – Leeks on shelf – Jeffery Martin, CC0, via Wikimedia Commons – retrieved from – https://commons.wikimedia.org/wiki/user:Veronicasgardentracker